Concealed Duct Fan Coil Units (2 pipe and 4 rows)
Water Chilled Fan Coil Units/Duct Fan Coil Units/Concealed Fan Coil Units (2pipe and 4 rows)
water chilled fan coil units
AC+FP 3.4 ÷ 23.8
|Supplyability||1000 sets per month|
|Payment||50% T/T as deposit rest before delivery|
|Packaging||Export Standard Package|
The FP series water chilled duct fan coil units are designed specially to meet the varied requirements of zone cooling or heating using chilled water or hot water. Fan coil can be applied to two pipe 3 rows or 4 rows systems to satisfy the requirements of a wide variety of air conditioning or heating application. The FP series is available in concealed versions for ceiling installation.
This unit is presented as a single block including: fan deck, cooling or cooling coil, removable filter, drip tray, electrical connection box.
FEATURES water chilled fan coil units
FRAME AND STRUCTURE
Water fan coil units Panels and frame are made of galvanized steel, properly punched and punched for fixing both accessories and the unit itself
Concealed fan coil The coils are made of seamless tubes expanded into aluminum fins in continuous block. The connections have brass headers with female fittings and provided with easily accessible vent and drainage valve.
Duct fan coil unit The fan decks are composed of double suction centrifugal fans with aluminum impellers and 3-speed fan motors. Each fan motor assembly is dynamically balanced.
The drip trays are made from sheet metal treated with polyester powder coating to ensure total resistance to atmospheric agents.
The easily removable filter is made of filtering honeycomb polypropylene fabric and supported by an aluminum frame. The filter is installed on the units with plenum only.
ELECTRICAL CONNECTION BOX
FCU All electric wires are connected to enclosed electrical terminal block, situated on the same side of the water connections.
2 pipe 4 rows
3 speed switch
ON-BOARD THERMOSTARTMechanical type for two pipe system exposed version use, working mode selection (OFF-Heating-Cooling), ventilation
NOMENCLATURE water chilled fan coil units
Fan coil Size Installation method: W: Horizontal Unit version A: Concealed version Water
connection L: Left hand R: Right hand Coil arrangement 1: 2 pipe 3 rows 2: 2 pipe 4 rows External static pressure --: Standard M: High static pressure (30Pa) H: High static
pressure (50Pa) Plenum air intake direction --: no plenum H: back air
A: Concealed version
L: Left hand
R: Right hand
1: 2 pipe 3 rows
2: 2 pipe 4 rows
External static pressure
M: High static pressure (30Pa)
H: High static pressure (50Pa)
Plenum air intake direction
--: no plenum
H: back air intake
* The data are referred to the following conditions:
Cooling: room temperature: 27 ºC 50% RH, water temperature: 7/12 ºC, high speed.
Heating: room temperature: 21 ºC, water inlet temperature: 60/50 ºC, high speed.